Xbc Diesel Fire Water Pump Set
|FOB Price:||US $5,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $5,000/ Piece|
|Transport Package:||Wood Case|
|Payment Terms:||T/T, D/P|
- Model NO.: XBC
- Air Engine Type: Diesel Engine
- Transmission: Direct Connection Transmission
- Diesel Fire Pump: Emergency Diesel Pumps
- Fire Fighting Pump: Diesel Pump
- Specification: ISO
- HS Code: 8413810090
- Type: Self-priming Pump With Inner Recirculation
- Theory: Gas-hydraulic Hybrid Type
- Structure: The Slide
- Clean Water Pump: Diesel Fire Fight Pump
- Trademark: Borra
- Origin: Wenzhou
Used for emergency water supply in high buildings, taper water, steel factories, wine plants, chemical factories, hotels. Automatic, full functions, good structure, easy to install and use.
as per conditions: 1-stage 1-priming centrifugal pump, high-pressure multi-stage pump, 2-priming pump.
1. Altitude: ≤2500m
2. Ambient temperature: -25~55ºC
3. Ambient relative humidity: 9~95%
4. Anti-earthquake degree: degree 7
5. Flow range: 50-700(L/S)
6. Head range: 32-600m
7. Power: 18-1100KW
8. Wet part materials: cast iron, graphite cast iron, stainless steel, cast copper.
Diesel engine fire pump, electric pumps and stabilized pressure pump can form an automatic voltage fire water supply system and can realize linkage with fire control center. When diesel engine fire pump group received orders, if utility without powertime, then automatically control cabinet of diesel power immediately to the starter of pump group issued open signal, the starter, enggine idle starting, then gradually adjust diesel engine accelerator and make the diesel engine speed until the rated speed. The control system will automatic monitoring of diesel engine, such as the workings of diesel oil, oil temperature, rotational speed and pump outlet pressure, etc. Through the automatic monitoring to determine whether the normal starting diesel, if starting failure criterion control system will be issued to start signal, if 13 times are starting, the automatic control system failure will be issued starting failure alarming. When diesel engine fire pump group received pipe pressure recovery or mains supplyicoil resume normal signal, pump group will rapidly slow down and in idle position monitor after a period of automatic stop.